GENERAC GENERATOR VIDEOS
THESE TWO PAGES [TOP OF PAGE AND BOTTOM] ARE SELECTOR GUIDES FOR CALCULATING PROPER GENERATOR WATTAGE NEEDED FOR YOUR PERSONAL SELECTIONS=
YOU CAN USE EITHER GUIDE TO ADD UP YOUR WATTAGE NEEDS TO DETERMINE WHAT SIZE GENERATOR WOULD FIT FOR YOU
KEEP IN MIND BIGGER IS BETTER -DON'T SHORT CIRCIUT YOUR NEEDS WITH SOMETHING THAT WON'T SUPPLY WHAT YOU SELECT, WHEN YOU NEED IT THE MOST
PAGE # 1
NOTE 1: This equipment has solid state circuitry and is extremely voltage sensitive. Make sure your generator yields less than 10% harmonic distortion of it's generated wave-form.
NOTE 2: These motor designs are shown as Code L, with high locked rotor values. A maximum starting watt value is generally (5) times running watts. However, some new air conditioner brands have realized more home standby plants are being purchased every year. A re-design in air conditioner starting loads, has begun, to lower this huge starting demand. If it's important to you, to have air conditioning during utility power blackout, consult licensed electrician to check locked rotor starting amps, to ensure air conditioner will start, while other loads are already in use.
NOTE 3: These motor designs are shown as Code G, with average locked rotor values. A maximum starting watt value is generally (3) times running watts.
NOTE 4: For large offices, using a multitude of UPS systems, always double the total UPS load for generator KW sizing.
PAGE # 2
Search by Keyword